Henan mau duct rubber compensator by rubber and fabric composite material limit, steel flanges, steel rods, it is mainly used for a variety of flexible connection between fan, air duct, its function is to shock absorption, noise reduction, displacement and sealing, medium resistance, easy installation, is a kind of very ideal environmental protection field shock absorption, noise reduction, the best accessories and smoke prevention and dust control.
1 、风道橡胶补偿器具有良好的反复位移 ( 变化 ) 还原性，能在较小尺寸范围内提供较大的多维方向补偿，能较好的消除各种管道安装连接时产 生的多向误差。
1, the air channel rubber compensator has good repeated displacement (change) reducibility, which can provide large multidimensional directional compensation in the smaller size range, and it can eliminate the multi-directional error produced by all kinds of pipeline installation and connection.
2. The air duct rubber compensator has the superior sound absorption and isolation function, and can effectively reduce and eliminate the transmission of sound and vibration of the system products such as boiler and fan.
3. The weak transmission loss of rubber and fiber reduces the design procedure and does not need to add other auxiliary facilities.
4, rubber and fiber fabric and heat insulation materials have high heat resistance and corrosion resistance, never rust, reduce maintenance costs.
5. The rubber compensator of the air duct has excellent air tightness and flexibility, and it can ensure that the conveying medium has no leakage and restores the original shape after repeated displacement.
1 、安装长度由用户在设计中选定，订货时未注明者按 L=350mm 的供货。
2 、表中重量按一般安装长度 L=350mm 计算。
3 、风道橡胶补偿器中间有支撑架，支撑架在安装前应保持不脱，待螺栓上紧后将其全部打掉，以保证安装合理，使其各项物理机械性能真正起到 作用。
A brief description of the installation of rubber compensator for air duct:
1, the length of the installation is selected by the user in the design, and the unmarked order is supplied by the L=350mm.
2. The weight in the table is calculated according to the general installation length of L=350mm.
3, the air channel rubber compensator has a support in the middle. The support rack should remain unchanged before installation. After the bolts are tightened up, they will be knocked out to ensure that the installation is reasonable, so that all physical and mechanical properties will really play a role.
The rubber material of the rubber compensator of the air channel can choose three kinds of natural rubber, three yuan ethylene propylene rubber and three silicone rubber. The three kinds of rubber temperature resistance is as follows: natural rubber is below 80 degrees, three yuan, ethylene propylene rubber is below 120 degrees, and silicone rubber is below 200 degrees.